This device has a micro switch which stimulates it's own particular blade. With this capability is able to control fluid flow inside the pipe by sending command to different electrical devices, such as pumps or electro motors or etc. This type of flow switch is S.P.D.T and is used in the non-flammable liquid line.
This type of flow switch can not be used in liquid pipe lines which have lower temperature than the freezing point.
To function properly, the bland must not grip to the bottom of pipe. So , choose suitable blades according to pipe size. Appropriate bland height for each pipe size can be observed in following diagram.
Flow switches type FS 16-01 have to be installed through 1" socket (rather vertically) at top side of the pipe line. If device is installed horizontally, the fluid flow should be upward. Because of gravity, device make an error in contrariwise installation.
Attention: Please, note to arrow on body for correct installation
Factory adjustment is set on minimum flow rang. Please, do not decrease the flow less than factory adjustment .otherwise , the flow switch dose not command to flow interruption.